be equipped with a BENTEL BA ( V – 4 A) Linear power supply or BENTEL SECURITY srl reserves the right to change the technical features of this . bentel jf. hello i have a fire security system bentel jf and i cant find the instaler manual or usser manual please can anibody help my thx. Bentel JF tulekahju signakeskus в категории: Рабочее оборудование, строительство, Другие машины и оборудование (ID номер.
|Published (Last):||12 September 2010|
|PDF File Size:||3.7 Mb|
|ePub File Size:||8.9 Mb|
|Price:||Free* [*Free Regsitration Required]|
What is this old floor. View your zone types to make sure that they actually have the right settings. The keystrokes you are writing out are the correct ones, but I don’t think that’s what you are actually entering. Newsletter Sign-Up Signup Email address. I would go into installer program and press to reset the module list first.
Or default the panel programming and start over. I’m not sure why you are unable to access location What could be causing this lack of entry delay? Find all posts by Microlab. I also changed the times: It’s also the voltage that the charger puts out. If it doesn’t, then you may have a failed zone input. Any ideas on why the bell goes off although during the entry delay period? It’s really easy to get one segment off with one of these things. Posted In General Chats and Discussions.
Tere, Kuidagi kindlast saan saata. I think you may have swapped a good battery for a failing one.
Bentel JF tulekahju signakeskus () –
I’m a bit worried that I have assigned zone 1 to a keypad but since I can’t enter section I can’t ’00’ the keypad zones out. Bentel J; Bentel Categories. The largest chip has the following: I wanted to make sure the keypad zones are null to eliminate the possibility of zone 1 being associated with a keypad, but when I try to enter section I get bentwl long error beep.
Another issue is that I have set the front door for entry delay but it sets the alarm off immediately.
DSC 5010 section 020 locked out?
If the zone closes, then it’s a field wiring issue. Is there a reset for the keypads? R, L8 on it. Find all posts by MrRonFL. I will try the jumper trick in a second and report back. Reprogram backto fire, let it go into trouble, put the resistor across the zone then reset the keypad. Soon my ‘monitoring’ neighbor is going to give up on me!
I recently added an extra keypad and reassigned all 3 keypads to 11,12 and You sounded like you were familier with the system, so it never occurred fo me the check that you had let the exit delay time out I had the same thing happen to me a few days ago with a fire zone. OK, I decided to go for it and did a software reset. Trying to hook up tire changer motor to switch.
You may not post new threads. Otherwise, simply jumper it closed. It is a CPI unit, which seems to be standard everything has always worked for me up until now anyway.
I had been opening the door immediately after arming because I had a house full of kids and didn’t want them to set off a bfntel sensor before I had a chance to check the door. Turn off light 6 in location Master code has been changed too.